These high-speed misters come in the form of a nebulizer mounted in the center and on the front of a large oscillating axial fan.
Operating principle: The rotary disc nebulizer sends fine droplets that are blown away by the fan wind and evaporate by absorbing heat.
The VBI mist ismounted on a column fan and are equipped with a peristalstaltic pump and a 15l tank. The water flow is 1 L/h.
The VBT mistis mounted on a table fan and is equipped with a peristalstical pump and provided without a tank. The water flow is 0.5 L/h.
Key technical features:
|Fan diameter||40 cm||45 cm|
|Fan flow||1200 m3/h||1500 m3/h|
|N Fan Speeds||3||3|
|Brumisation debit||1 L/h||1 L/h|
|Refrigeration power||0.7 KW||0.7 KW|
|Control of brumisation||Switch||Switch|
|Sound level||52 dB||56 dB|
|Separate control of brumisation and ventilation||Yes||Yes|
- Connection to the electrical grid by plug 2P-T 6A
Use temperature: For perfect evaporation of the drops, it is recommended to use the nebulizer when the temperature exceeds 26oC.